Important Update - Suburban RV_Caravan Gas Fuelled Water Heaters
14 September 20
Important Update : Suburban RV/Caravan Gas Fuelled Water Heaters
All Gas work licence holders,
This communication is to update you on the current situation relating to Suburban gas fuelled water heaters and the suspension of approval certificate AGA4624.
Check the Australian Competition and Consumer Commission (ACCC) recall advert for information: https://www.productsafety.gov.au/recall/coast-rv-pty-ltd-suburban-recreational-vehicle-water-heaters-model-sw6pa-sw6dea-sw6da-sw4dea-sw4da-sw4deca-and-sw6deca
Suburban Water Heaters within the recall range (check the recall details) must be inspected by a gas work licence holder in line with the ‘Coast to Coast caravan and leisure Safety Recall Inspection Procedure’ to ensure the:
- unit has a correctly formed flange and it is correctly installed; AND
- calculated CO/CO2 ratio is below the allowance of 0.01 during the combustion testing; AND
- operational CO level in the living space was not higher than the baseline CO level in the procedure.
On completion of the inspection, the gas work licence holder should complete all documentation required by the procedure.
Units that have been inspected and found to be safe can be identified by a sticker attached as part of the procedure.
Where the appliance has been disconnected by others, and is reconnected for the purpose of the inspection and testing, the gas work licence holder should issue a Gas System Compliance Certificate (PGA734) to the owner (or person in possession of the vehicle) stating that;
‘An inspection has been completed in line with the ‘Coast to Coast caravan and leisure Safety Recall Inspection Procedure’, the appliance has been reconnected to the gas system and tested to ensure combustion products are within acceptable levels and not leaking into the living space’.
Inspections of caravans and recreational vehicles for sale, resale or change of ownership
* Suburban Water Heaters within the recall range cannot be certified as part of a gas safety inspection. Unless the unit has already been inspected, identified by the sticker next to the model and serial number marked CTC001.
* Suburban Water Heaters NOT within the product recall range should be checked to ensure safe operation, including correct combustion and that there is no infiltration of combustion products into the living area, as part of the compliance inspection and testing prior to issuing a Gas System Compliance Certificate.
What should you do if a customer contacts you in relation to this situation?
- Advise the customer to check the latest ACCC product safety recall advertisement. If the appliance is one of those identified they should cease using the appliance and contact Coast to Coast.
The Petroleum and Gas Inspectorate safety alert 94 https://www.business.qld.gov.au/industries/mining-energy-water/resources/safety-health/petroleum-gas/safety-news-education/alerts-instructions
Information from the Australian Competition and Consumers Commission (ACCC) https://www.productsafety.gov.au/recall/coast-rv-pty-ltd-suburban-recreational-vehicle-water-heaters-model-sw6pa-sw6dea-sw6da-sw4dea-sw4da-sw4deca-and-sw6deca
The ACCC product safety recall https://www.productsafety.gov.au/system/files/recall/Recall%20Advertisement%20-%20updated%20July%202020_3.pdf
Any changes to the quantity and scope of affected product and any further information in relation to the ACCC safety product recall or PGI safety alert will be provided when available.
Principal Inspector Gas work
Most Popular Articles
Number of news items returned: 1 to 15 records of 120
24 August 2017
If you're a gas work licence/authorisation holder, you'll be pleased to know that the amendment to AS/NZS 1596:2014 The Storage ...
20 July 2017
Have you seen the new Queensland Globe? The Queensland Globe is an online interactive tool that turns physical, geographical and spatial ...
PRODUCT SAFETY RECALL: Thetford 3-Way Absorption fridges, fitted into caravans and motorhomes. The gas control valve pressure test point nut may not be correctly tightened it could cause a gas leak, potentially leading to a fire.
27 March 2018
PRODUCT SAFETY RECALL: Thetford 3-Way Absorption fridges, fitted into caravans and motorhomes. The gas control valve pressure test point nut ...
22 May 2017
A Product Safety Recall notice, has been issued for Rinnai “Symmetry” inbuilt gas log effect space heaters as pictured below, ...
15 November 2019
Published today from Product Safety Australia - RECALLS Coast RV Pty Ltd — Suburban Recreational Vehicle Water Heaters Model SW6DEA, SW6DA, ...
24 November 2016
01 December 2016
Our 2016 AGM was held 30 November 2016 The following Officer Bearers were elected Executive Committee President Darrel Vecchio Vice President Kent Vickers Secretary Kurt ...
31 January 2017
Queensland Gas Association are the proud sponsors of the Type B Gas Installation of the Year & Commercial Gas Installation of ...
06 February 2017
Our first General Meeting of 2017 will be held in Brisbane on Thursday the 2nd of March , 5.30pm for a ...
05 December 2016
Please be advised that the Office of the Queensland Gas Assoc Inc. will close at 2.30pm on Friday 23rd December ...
13 October 2016
Our fifth General Meeting of 2016 will be held in Brisbane on Tuesday the 18th of October , 5.30pm for ...
10 January 2017
Hello and Welcome 2017! From the team at QGA, we hope you had an enjoyable festive season, a happy New Year ...
16 February 2017
Attend your local consultation session: North Brisbane 21 February Gold Coast 22 February Logan 23 February Morningside 24 February Ipswich 7 March Charters Towers 9 March Mackay ...
20 October 2016
Our Annual General Meeting will be held from 6.00pm to 7.30pm. Please join us afterwards for complimentary dinner & drinks @ ...
13 October 2016
Applications for Individual Type A Gas Device Approvals are now to be submitted online. Please click on the " Gas Approvals" ...